Funny I came on to post a question about receptacles within 6' of a sink. I have been writing contractor's to GFI receptacles on other than Dwelling units when the receptacle is within 6' of the sink such as a Garbage disposal, insta hot, microwave, etc. 210.8A(7) They added a word change to make it clear that a receptacle within 6' of ANY sink requires GFI protection. They changed or added the word WHERE to the sentence to be identical to 2108B(5). My thought is if we have to enforce it on Dwelling units, what is the difference? Some contractors giving me a hard time about this, but I don't see any exception that says if behind a door don't do it. Also in my opinion a GFI receptacle under a sink behind a door is still readily accessible.